Main rangePowerLogic product namePowerLogic PM8000 device short namePM8243 product or component typePower meter Complementary power quality analysisconforming to EN 50160: 2010 compliance report conforming to IEEE 519: 2014 compliance report conforming to IEC 61000-4-30: class S power quality measurement up to the 63rd harmonic harmonic distortion waveform capture voltage sag and swell detection programmablity (logic and math functions) conforming to IEC 62586 power quality monitoring device applicationWAGES meteringPower monitoring type of measurementCurrentVoltageFrequencyActive and reactive power totalApparent power totalPower factor totalActive and reactive power per phase, rmsApparent power per phase, rmsPower factor per phase, rms supply voltage90...415 V AC 45...65 Hz +/- 10 %110...415 V DC +/- 10 % network frequency50 Hz60 Hz [In] rated current1 A10 A5 A poles description1P + N3P + N3P power consumption in VA18 VA at 415 V AC display typeWithout display sampling rate256 samples/cycle measurement current50…10000 mA analogue input typeVoltage (impedance 5 MOhm)Current (impedance 0.3 MOhm) measurement voltage57…400 V AC 42...69 Hz between phase and neutral100…690 V AC 42...69 Hz between phases frequency measurement range42…69 Hz number of inputs3 digital 30 V AC3 digital 60 V DC measurement accuracyCurrent +/- 0.1 %Voltage +/- 0.1 %Active energy +/- 0.2 % accuracy classClass 0.2S active energy conforming to IEC 62053-22Class 0.2 active energy conforming to ANSI C12.20Class 0.2 active power conforming to IEC 61557-12Class 0.5S reactive energy conforming to IEC 62053-24Class 0.5 power factor conforming to IEC 61557-12Class 0.2 voltage conforming to IEC 61557-12Class 0.2 current conforming to IEC 61557-12 number of outputs1 pulse information displayedVoltageCurrentFrequencyPowerEnergy consumptionHarmonic distortion communication port protocolModbus RTU at 115 kbauds - 2-wireION at 115 kbauds - 2-wireDNP3IEC 61850Modbus TCP/IPEthernet Modbus TCP/IP daisy chain at 10/100 Mbit/sRSTP 801.1d 2004 communication port supportEthernetScrew terminal block: RS485 communication network typeIPv6 (internet protocol) data recordingHarmonics logsSag and swell logsGPS synchronisationTime stampingData logsTrending/forecastingWaveform logsAlarm logsSequence of event recordingMin/max of instantaneous valuesEvent logs memory capacity512 MB web servicesCustomizable home pageFile upload/download via FTPFile upload/download via SFTPWeb serverAlarm notification by e-mailViewing of captured waveform (FTP)Viewing of captured waveform (web)HTTPS server communication serviceSMTP e-mail notificationDHCPRSTP supportNTP time synchronizationPTP time synchronization cybersecurityPassword protectionPort hardeningEnable/disable communication portsRobust security logsSyslog protocol support mounting modeClip-on mounting supportDIN rail installation categoryIII Safety ConstructionIII, 400…690 V conforming to IEC 61010-1:ed. 3III, 400…690 V conforming to EN 61010-1:ed. 3III, 347…600 V conforming to UL 61010-1:ed. 3III, 347…600 V conforming to CSA C22.2 No 61010-1:ed. 3 standardsIEC 61557-12IEC 62052-11IEC 62053-22IEC 62053-24IEEE 1588IEC 62586-2IEC 61326-1 product certificationsCECULusN998China RoHS width90.5 mm depth90.8 mm height90.5 mm net weight528 g Environment electromagnetic compatibilityElectrostatic discharge conforming to IEC 61000-4-2Radiated radio-frequency electromagnetic field immunity test conforming to IEC 61000-4-3Electrical fast transient/burst immunity test conforming to IEC 61000-4-4Surge immunity test conforming to IEC 61000-4-5Conducted RF disturbances conforming to IEC 61000-4-6Magnetic field at power frequency conforming to IEC 61000-4-8Voltage dips and interruptions immunity test conforming to IEC 61000-4-11Immunity to impulse waves conforming to IEC 61000-4-12Conducted and radiated emissions conforming to EN 55022Conducted and radiated emissions conforming to EN 55011Conducted and radiated emissions conforming to FCC part 15Conducted and radiated emissions conforming to ICES-003Conducted RF disturbances (2...150 Hz) conforming to CLC/TR 50579Surge withstand conforming to IEEE C37.90.1 IP degree of protectionIP30 conforming to IEC 60529 relative humidity5…95 % ambient air temperature for operation-25…70 °C ambient air temperature for storage-40…85 °C operating altitude3000 m Offer Sustainability REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My Documentsprp.document.label.format pdfSize 167.3 KBDate 11/1/19DescriptionThis document describes the process to upgrade RD96 display firmware to the latest version for use with PowerLogic™ ION9000, PM8000 or ION7400 series meters.prp.document.label.format pdfSize 5 MBDate 11/1/19DescriptionThe document explains the configuration and operation of the PM8000 series meters.prp.document.label.format pdfSize 947.6 KBDate 11/1/19DescriptionThis document describes the process to upgrade PowerLogic™ ION9000, PM8000 or ION7400 series meters to the latest firmware version. It also contains information about upgrading analog I/O option module firmware.prp.document.label.format pdfSize 95.2 KBDate 11/1/19DescriptionThis update provides a summary of technological advances in the Power and Energy Monitoring System offers, and the technical documentation accompanying their release.prp.document.label.format pdfSize 112.4 KBDate 9/1/19DescriptionThis technical note outlines the compliance of applicable PowerLogic meters with the International Electrotechnical Commission’s IEC 61000-4-30 (or “4-30”) standard, and is intended for personnelwith knowledge of power quality and power quality standards.prp.document.label.format pdfSize 92.4 KBDate 2/1/19DescriptionWhats New in PM8000 v2.1.0 firmware. The following new features are included: Enhanced firmware upgrades, PTP time synchronization, Secure webserver (HTTPS), otherprp.document.label.format pdfSize 97.7 KBDate 12/5/17DescriptionFirmware version v1.4.1 for the PM8000 series meter adds security enhancements, new communications functionality, increased onboard log storage capacity, a webpage waveform viewer and other improvements.prp.document.label.format pdfSize 188 KBDate 7/1/16DescriptionFirmware version v1.3.1 for the PM8000 series meter adds Internal clock temperature compensation feature and resolves previously unknown Modbus master issue. This document also contains IPv6 global addressing and IPv6 gateway support content from the previous what's new document (7EN12-0295).CADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsHandoutFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages25
Software and FirmwareLanguage
Firmware - ReleasedFormatSizeAdd to My Documentsprp.document.label.format s19Size 220.8 KBDate 3/5/19DescriptionThe 1.2.0 (V001.002.000) firmware for the METSEPM89M0024 Analog I/O Module adds 0-20 mA support when used with PM8000, ION7400, or ION9000 meter firmware 2.1.0 (V002.001.000) or higher. SHA256 File signatures:77855de93e70ed9b25be9568b64eaa333c56ead286624323fbc04073cdb5626a *METSEPM89M0024_AIO_V001.002.000_Release.s19prp.document.label.format s19Size 220.8 KBDate 3/5/19DescriptionThe 1.2.0 (V001.002.000) firmwarefor the METSEPM89M2600 Digital I/O Module is compatible with PM8000, ION7400, and ION9000 meters.SHA256 File signatures:5f88067ed29ef9d7c369410fb1785967cf1838436062a0509c6aee1ad7f0c412 *METSEPM89M2600_DIO_V001.002.000_Release.s19prp.document.label.format zipSize 28.7 MBDate 3/4/19Files in document286 KBzip28.2 MB166.7 KBDescriptionFirmware version 2.1.0 for the PowerLogic™ PM8000 series meter adds enhanced firmware upgrade support, PTP, Secure HTTPS webserver, ION Module updates, updated support for the latest versions of EN50160, IEEE 519 and IEC 61000-4-30 power quality standards, pre- and post-event data capture for data and waveform recorders, and 0-20 mA support for the Analog I/O option module.To upgrade your meter to firmware version 2.1.0, you must use ION Setup version 3.1 or later. Please refer to the “Upgrading devices to firmware v2.1.0” technical note at https://www.se.com/ww/en/download/document/7EN72-0203/ for instructions on upgrading your meter firmware to version 2.1.0.SHA256 File signatures:3cdd6e69bfa85d8b76255391270db77f504ec77385bd2dfbc3c7f6b62f31c097 *PM8000_V002.001.000.zipprp.document.label.format zipSize 6.1 MBDate 2/21/19Files in documentbin5.8 MBDescription"Some RD96 displays may require a two-step firmware upgrade for compatibility with the ION9000 series meter. The RD96 display firmware must be upgraded with the rmdupg_rd96s_001.000.000_patch.bin file before proceeding with the standard rmdupg_rd96_004.000.000.bin display firmware upgrade file.See the ""RD96 Display upgrade using ION9000 meter.pdf"" document and the Power Meter user manual for additional information and display firmware upgrade instructions.Note: This remote display OS firmware is not compatible with PM8000 & ION7400 meters running firmware versions 1.4.x and older.SHA256 File signatures:59c394c2c4f62cd2bb70ec2331b11ad0a03375818b83274c14ac6f8dc5644f82 *rmdupg_rd96s_001.000.000_patch.bin83c30aca20c42622d99aced8f2981ec75de63021887750a6ba7e390aded68354 *RD96 Display upgrade using ION9000 meter.pdf"prp.document.label.format binSize 5.8 MBDate 10/16/18DescriptionThis is OS Package version 4.0.0 for the METSEPM89RD96 remote display. It supports meter firmware version 2.0.0, including the PowerLogic™ ION9000 series.See the Power Meter user manual for display firmware upgrade instructions.Note: This remote display OS Package is not compatible with PM8000 & ION7400 meters running firmware versions 1.4.x and older.SHA256 File signatures:8b0aaa760d1e705b7528ee3941e381c00cab3adc524b460a9fd04acf54a0ef37 *rmdupg_rd96_004.000.000.binprp.document.label.format binSize 5.6 MBDate 10/16/18DescriptionThis is OS Package version 3.2.193 for the METSEPM89RD96 remote display. It supports PowerLogic™ PM8000 and ION74000 series meters with firmware versions 1.4.x and older.See the Power Meter user manual for display firmware upgrade instructions.Note: This remote display OS Package is not compatible with meters running firmware versions 2.0.0 and newer.SHA256 File signatures:c55b87fda044cc5def860129c460d87f6c57560868315f4454306c8a49efef67 *rmdupg_rd96.003.002.193.bin
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.