Main range of productEasyPact MVS rangeEasyPact product nameMVS08H device short nameMVS08H product or component typeCircuit breaker device applicationDistribution poles description3P protected poles description3P 3d network typeAC breaking capacity codeH suitability for isolationYes conforming to IEC 60947-2 utilisation categoryCategory B trip unit nameET6G trip unit technologyElectronic trip unit rating800 A Complementary network frequency50/60 Hz control typeManually operated mounting modeFixed mounting supportRailBase plate connection positionVerticalHorizontal location of connectionRear [In] rated current800 A at 40 °C [Ui] rated insulation voltage1000 V AC 50/60 Hz conforming to IEC 60947-2 [Uimp] rated impulse withstand voltage12 kV conforming to IEC 60947-2 [Ue] rated operational voltage690 V AC 50/60 Hz conforming to IEC 60947-2 circuit breaker CT rating800 A breaking capacity65 kA Icu at 220...440 V AC 50/60 Hz conforming to IEC 60947-2 [Ics] rated service breaking capacity65 kA (Ics) at 220...440 V AC 50/60 Hz conforming to IEC 60947-250 kA (Ics) at 690 V AC 50/60 Hz conforming to IEC 60947-2 mechanical durability20000 cycles (with maintenance) conforming to IEC 60947-210000 cycles (without maintenance) conforming to IEC 60947-2 electrical durabilityCategory B: 6000 cycles 440 V AC 50/60 Hz without maintenance conforming to IEC 60947-2Category B: 4000 cycles 690 V AC 50/60 Hz without maintenance conforming to IEC 60947-2 connection pitch115 mm without spreader contact position indicatorYes [Icm] rated short-circuit making capacity143 kA (Icm) at 220...440 V AC 50/60 Hz conforming to IEC 60947-2 [Icw] rated short-time withstand current65 kA (1 s) at 220...440 V AC 50/60 Hz conforming to IEC 60947-250 kA (1 s) at 690 V AC 50/60 Hz conforming to IEC 60947-236 kA (3 s) at 440/690 V AC 50/60 Hz conforming to IEC 60947-2 trip unit protection functionsLSIG protection typeInstantaneous short-circuit protectionEarth faultShort time short-circuit protectionOverload protection (long time) fault indicationInternal faultShort-circuitEarth faultOverload long time pick-up adjustment type IrAdjustable 9 settings long time pick-up adjustment range0.4...1 x In long time delay adjustment typeAdjustable 9 settings [tr] long-time delay adjustment range0.5…24 s at 6 x Ir short-time pick-up adjustment type IsdAdjustable 9 settings [Isd] short-time pick-up adjustment range1.5...10 x Ir short-time delay adjustment typeAdjustable 5 settings [tsd] short-time delay adjustment range100…400 ms instantaneous pick-up adjustment type IiAdjustable 9 settings instantaneous pick-up adjustment range2...15 x InOff ground-fault pick-up adjustment typeAdjustable 9 settings ground-fault time delay adjustment type -tgAdjustable 5 settings [tg] ground-fault time delay adjustment range100…400 ms [Ig] ground-fault pick-up adjustment range0.2...1 x In zone selective interlocking ZSIWith current sensor rating range400/2000 A maximum breaking time25 ms maximum closing response time70 ms height352 mm width422 mm depth297 mm net weight40 kg Environment standardsIEC 60947-2 product certificationsIECCCCCCSGOST IP degree of protectionIP40 pollution degree4 conforming to IEC 60664-1 ambient air temperature for operation-5…70 °C ambient air temperature for storage-40…85 °C without control unit-25…85 °C with control unit Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages9
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.