Main range of productEasyPact MVS rangeEasyPact product nameMVS10HA device short nameMVS10HA product or component typeSwitch disconnector device applicationDistribution poles description3P network typeAC suitability for isolationYes conforming to IEC 60947-2 utilisation categoryAC-23A Complementary network frequency50/60 Hz control typeElectrically operated mounting modeFixed mounting supportRailBase plate connection positionHorizontalVertical location of connectionRear [Ie] rated operational currentAC-23A: 1000 A AC 50/60 Hz 690 V rated dutyContinuous [Ui] rated insulation voltage1000 V AC 50/60 Hz conforming to IEC 60947-3 [Uimp] rated impulse withstand voltage12 kV conforming to IEC 60947-3 [Icw] rated short-time withstand current65 kA during 1 s conforming to IEC 60947-3 at -5…70 °C36 kA during 3 s conforming to IEC 60947-3 at -5…70 °C [Icm] rated short-circuit making capacity143 kA AC at 50/60 Hz [Ue] rated operational voltage690 V AC 50/60 Hz conforming to IEC 60947-3 contact position indicatorYes mechanical durability20000 cycles with maintenance conforming to IEC 60947-310000 cycles without maintenance conforming to IEC 60947-3 electrical durabilityAC-23A: 6000000 cycles 440 V AC 50/60 Hz without maintenance conforming to IEC 60947-3AC-23A: 4000000 cycles 690 V AC 50/60 Hz without maintenance conforming to IEC 60947-3 connection pitch115 mm without spreader height352 mm width422 mm depth297 mm net weight40 kg Environment standardsIEC 60947-3 product certificationsCCCGOSTIECCCS IP degree of protectionIP40 pollution degree4 conforming to IEC 60664-1 ambient air temperature for operation-5…70 °C ambient air temperature for storage-40…85 °C without control unit Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My Documents
- All Languages6
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.