Main range of productEasyPact MVS rangeEasyPact product nameMVS10NA device short nameMVS10NA product or component typeSwitch disconnector device applicationDistribution poles description4P neutral positionLeft network typeAC suitability for isolationYes conforming to IEC 60947-2 utilisation categoryAC-23A Complementary network frequency50/60 Hz control typeElectrically operated mounting modeDrawout mounting supportBase plateRail connection positionHorizontalVertical location of connectionRear [Ie] rated operational currentAC-23A: 1000 A AC 50/60 Hz 690 V rated dutyContinuous [Ui] rated insulation voltage1000 V AC 50/60 Hz conforming to IEC 60947-3 [Uimp] rated impulse withstand voltage12 kV conforming to IEC 60947-3 [Icw] rated short-time withstand current50 kA during 1 s conforming to IEC 60947-3 at -5…70 °C25 kA during 3 s conforming to IEC 60947-3 at -5…70 °C [Icm] rated short-circuit making capacity105 kA AC at 50/60 Hz [Ue] rated operational voltage690 V AC 50/60 Hz conforming to IEC 60947-3 contact position indicatorYes mechanical durability20000 cycles with maintenance conforming to IEC 60947-310000 cycles without maintenance conforming to IEC 60947-3 electrical durabilityAC-23A: 6000000 cycles 440 V AC 50/60 Hz without maintenance conforming to IEC 60947-3AC-23A: 4000000 cycles 690 V AC 50/60 Hz without maintenance conforming to IEC 60947-3 connection pitch115 mm without spreader height439 mm width556 mm depth395 mm net weight85 kg Environment standardsIEC 60947-3 product certificationsIECGOSTCCSCCC IP degree of protectionIP40 pollution degree4 conforming to IEC 60664-1 ambient air temperature for operation-5…70 °C ambient air temperature for storage-40…85 °C without control unit Contractual warranty Warranty18 months
CADFormatSizeDateAdd to My DocumentsCertificateFormatSizeDateAdd to My DocumentsDeclaration of conformityFormatSizeDateAdd to My DocumentsEnd of Life InformationFormatSizeDateAdd to My Documents
- All Languages7
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.