Main range compatibilitySpacialThalassa Type of filterG2 Flow rateFree flow rate with standard filter: 165 m3/h at 50 HzFree flow rate with standard filter: 193 m3/h at 60 Hz input voltage230 V 50/60 Hz CertificationCEEACREACHRoHSEMC directive 89/336 EEC Complementary Absorbed power15.5 W 50 Hz14.4 W 60 Hz [In] rated current0.2 A 50 Hz0.18 A 60 Hz bearing typeBall height268 mm external: width248 mm external: depth104 mm external: cut-out dimensions223 x 223 mm net weight1.4 kg materialOutlet grille: injected thermoplastic (PC)Motor support: injected thermoplastic (ASA PC) colourOutlet grille: smoked black (RAL 9005)Motor support: black (RAL 9005) ambient air temperature for operation-20…60 °C ambient air temperature for storage-40…70 °C maximum pressure50 Pa flow rate 0 m³/h connections - terminalsFaston connector device composition1 axial motor1 external protective transparent smoked grille: front1 smart filter with dust sensor1 fan sensor ready to be mounted: rear of outlet grille1 cable gland1 cut-out template condition of useFilter must be cleaned and replaced regularlyFlow rates depends on the work point, see ProClima softwareOverfrequent filter replacement should be avoidedSurrounding environment must be relatively cleanOutside temperature must be 5 °C lower than inside temperature Offer Sustainability REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
CatalogueFormatSizeAdd to My DocumentsBrochureFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages9
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.