Main rangePratiKa product or component typeSocket device short namePratiKa socket plug, socket categoryLow voltage poles description3P + N + E network typeAC outlet standardIndustrial Complementary mounting modePanel-mounted plug, socket, control station shapeAngled [In] rated current16 A [Ue] rated operational voltage380...415 V network frequency50/60 Hz ground lug clockwise position6 h plug, socket materialHousing: self-extinguishing engineering polymer contacts materialSleeves: brass connections - terminalsCaptive screws cable cross section1…4 mm² net weight0.207 kg base dimension90 x 100 mm height100 mm width90 mm depth106 mm colourGrey (RAL 7035) voltage colourRed Environment standardsIEC 60309-1IEC 60309-2 IP degree of protectionIP44 conforming to IEC 60529 IK degree of protectionIK08 conforming to EN 62262 fire resistance850 °C conforming to IEC 60695-2-1 relative humidity50 % at 40 °C70 % at 30 °C90 % at 20 °C ambient air temperature for operation35 °C ( 86400 s ) Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight173.9 g Package 1 Height8 cm Package 1 width9 cm Package 1 Length9.9 cm Unit Type of Package 2BB1 Number of Units in Package 210 Package 2 Weight1.908 kg Package 2 Height18 cm Package 2 width27 cm Package 2 Length27 cm Unit Type of Package 3S03 Number of Units in Package 320 Package 3 Weight4.481 kg Package 3 Height30 cm Package 3 width30 cm Package 3 Length40 cm Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Contractual warranty Warranty18 months
CatalogueFormatSizeDateAdd to My DocumentsCADFormatSizeDateAdd to My DocumentsChina RoHS declarationFormatSizeDateAdd to My DocumentsDeclaration of conformityFormatSizeDateAdd to My Documents
- All Languages5
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.