Main rangePragma product or component typeEnclosure enclosure typeDistribution enclosure width486 mm height480 mm wall: 510 mm outside: depth86 mm wall: 23 mm outside: Nb of 18 mm modules per row18 Nb of horizontal rows2 electrical insulation classClass IIDouble insulation provided equipment2 x terminal block1 x identification label1 x marking kit1 x blanking plate strip Type of doorWithout Complementary enclosure mountingFlush 9 mm pitches36 total number of 18 mm modules36 power dissipation in W62 W [In] rated current90 A [Ui] rated insulation voltage400 V type of railDIN mounting plate descriptionWithout mounting plate cable entryCable or tubeRemovable platesSide pre-cutouts number of terminal blocks1 earth (Quick) with 24 outgoers1 neutral (Quick) with 24 outgoers distribution block outgoers3 x 25 mm² for earth21 x 4 mm² for earth3 x 25 mm² for neutral21 x 4 mm² for neutral enclosure materialBack part: technoplasticFront face: technoplastic colourEnclosure: white (RAL 9016)Front face: grey (RAL 7004) targeted countryCzech republicRussiaGreeceHungary embedding depth86 mm internal depth84 mm Environment fire resistanceBack part: 650 °CFront face: 650 °C IP degree of protectionIP30 without doorIP40 with door IK degree of protectionIK08 without doorIK09 with door environmental characteristicHalogen free overvoltage categoryII ambient air temperature for operation-25…60 °C standardsIEC 60670-1IEC 60670-24IEC 61439-1IEC 61439-3 Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Contractual warranty Warranty18 months
China RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.