View all Resi9 DB60
Circuit breaker for service connection - DB60 - 1P+N - 45AShow more characteristics
has not been replaced. Please contact your customer care center for more information.
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main Range of productResi9 product nameDB60 product or component typeCircuit-breaker device location in systemMain incomer Pole1P + N Maximum current rated45 A Settings45 A 9 kVA30 A 6 kVA15 A 3 kVA neutral positionLeft standardsNF C 62-412 electrical insulation classClass II network typeAC trip unit technologyThermal-magnetic Safety functionCover opening open Complementary network frequency50 Hz [Ue] rated operational voltage250 V AC 50 Hz conforming to NF C 62-412 breaking capacity2 kA contact position indicatorYes control typeToggle mounting supportMounting plate height209 mm width71 mm depth73 mm mechanical durability5000 cycles electrical durability1000 cycles conforming to NF C 62-412 provision for padlockingYes Type of connectionFixed terminal 30°, cable cross section: 1.5…16 mm² tightening torqueSetting: 1 N.mPower terminals: 3.5 N.m earth-leakage protectionWithout Environment IP degree of protectionIP40 (front face) relative humidity90 % at 40 °C ambient air temperature for operation-5…40 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins
CADFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.