Main rangeEcoStruxure Building Expert product nameSE7000 Series device short nameSE7600B product or component typeRoom controller device applicationLow voltage rooftop product specific application2-stage heating2-stage cooling sensor type10 kOhm T2 NTC thermistor measurement range: +/- 0.2 °F PIR coverWithout cover Complementary range compatibilitycommunication card sensor temperature sensor relay sensor coverplate [Us] rated supply voltage10...30 V AC 50/60 Hz rated operational power in VA2 VA electrical insulation classClass II network frequency50 Hz60 Hz communication port protocolBACnet MS/TP temperature setting range40…90 °F heating0.9 °F per step54…100 °F cooling information displayedTemperature: - 40...122 °F Control accuracyTemperature: +/- 0.9 °F, (at 70 °F typically calibrated) number of inputs2 dry contact number of outputs2 universal Output ratingFor digital output: 30 V AC, 1 A (maximum) For digital output: 30 V AC, 3 A (inrush) For analog output: 0...10 V DC, <= 5 mA into >= 2 kOhm proportional bandFor heating: adjustable P regulator by 2 °F (factory setting) For cooling: adjustable P regulator by 2 °F (factory setting) contact operation5 standard push-button AWG gaugeAWG 22...AWG 18 connections - terminalsScrew terminal width3.42 in depth1.18 in height4.92 in product weight0.75 lb(US) Environment relative humidity0…95 %, non-condensing (operating)0…95 %, non-condensing (storage) ambient air temperature for operation32…122 °F ambient air temperature for storage-22…122 °F standardsFCC part 15 subpart BUL 873CSA C22.2 No 24ICES-003 product certificationsFCC conforming to CFR 47 part 15 class ACEC-Tick conforming to AS/NZS CISPR 22UL listed file E27734 CCN XPAXUL listed file E27734 CCN XPAX7 directives89/336/EEC - electromagnetic compatibility Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Environmental Disclosure Circularity Profile
EU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages4
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.