- Reason for Substitution: End of life
- Substitution date: 14 February 2014
Main product or component typePassive filter product specific applicationReduction of current harmonics Complementary range compatibilityAltivar 61Altivar 71 [Us] rated supply voltage480 V +/- 10 % power supply frequency60 Hz +/- 5 % quantity per drive1 filter per drive for ATV61HU40N41 filter per drive for ATV61HU55N41 filter per drive for ATV61WU40N41 filter per drive for ATV61WU40N4C1 filter per drive for ATV61WU55N41 filter per drive for ATV61WU55N4C1 filter per drive for ATV71HU40N41 filter per drive for ATV71HU55N41 filter per drive for ATV71PU40N4Z1 filter per drive for ATV71PU55N4Z1 filter per drive for ATV71WU40N4 [In] rated current10 A network number of phases3 phases THDI10 % for ATV61HU40N4 ATV61H motor: 4 kW/5 hp10 % for ATV61HU55N4 ATV61H motor: 5.5 kW/7.5 hp10 % for ATV71HU40N4 ATV71H motor: 4 kW/5 hp10 % for ATV71HU55N4 ATV71H motor: 5.5 kW/7.5 hp10 % for ATV71PU40N4Z ATV71P motor: 4 kW/5 hp10 % for ATV71PU55N4Z ATV71P motor: 5.5 kW/7.5 hp10 % for ATV71WU40N4 ATV71W motor: 4 kW/5 hp5 % for ATV61WU40N4 ATV61W motor: 4 kW/5 hp5 % for ATV61WU40N4C ATV61W motor: 4 kW/5 hp5 % for ATV61WU55N4 ATV61W motor: 5.5 kW/7.5 hp5 % for ATV61WU55N4C ATV61W motor: 5.5 kW/7.5 hp max current1.5 x nominal current efficiency98 % cos phi1 (150 % of line current)0.85 (75 % of line current)0.99 (100 % of line current) electrical connectionterminal, connection capacity: 16 mm² electrical insulation classClass F net weight27 kg Environment IP degree of protectionIP20 relative humidity5…85 % without condensation ambient air temperature for operation40…55 °C (with current derating 3 % per °C)5…40 °C (without current derating) ambient air temperature for storage-25…55 °C operating altitude<= 1000 m without current derating> 1000...4000 m with current derating 5 % per 1000 m Packing Units Package 1 Weight20.000 kg Package 1 Height3.500 dm Package 1 width3.700 dm Package 1 Length5.700 dm Contractual warranty Warranty18 months
- All Languages1
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.