View all Preventa XPS MF
Modicon M580 - ePAC Controller - Ethernet Programmable Automation Controller & Safety PLC PLC for process, high availability & safety solutions Modicon M580 ePAC is the controller which can help hybrid manufacturers achieve better, measurable, earlier ROI and Up to 100% returns on their project investments in less than three months.
- Reason for Substitution: End of life
- Substitution date: 01 January 2020
Main range of productPreventa Safety automation product or component typePreventa safety remote mixed I/O module safety module nameXPSMF3 safety module applicationExtension of I/O capacity safety use categoryCategory 4 maximum conforming to EN 954-1Performance level e conforming to EN/ISO 13849-1SIL 3 conforming to EN/IEC 61508 function of moduleMonitoring safety actuators for discrete inputMonitoring safety actuators for discrete outputMonitoring safety detection for discrete inputMonitoring safety dialogue for discrete inputMonitoring safety dialogue for discrete outputMonitoring short-circuit and line break for line control outputs [Us] rated supply voltage24 V DC - 15...20 % supplySELV or PELV conforming to EN/IEC 60950 discrete input number16 not isolated discrete input(s) number of outputs2 not isolated for line control outputs discrete output number16, not isolated structure type10BASE-T/100BASE-TX Complementary response timeDepending on size of application associated fuse rating16 A, slow-blow voltage state 0 guaranteed<= 5 V for discrete input voltage state 1 guaranteed15...< 30 V for discrete input current state 0 guaranteed1...1.5 mA (discrete input) current state 1 guaranteed<= 2 mA (discrete input) discrete input voltage20 V discrete input current40 mA input protection typeProtected against short-circuit output voltage20 V line control outputs nominal output current60 mA for line control outputs switching voltage7.5 V for discrete input switching time250 µs discrete output voltage24 V DC output voltage tolerance+/- 3 % discrete output current> 10 mA at 60 °C (channels 1 to 3, 5 to 7, 4 and 8)1 A at 60 °C (channels 1 to 3, 5 to 7, 4 and 8)2 A at 40 °C (channels 1 to 3, 5 to 7, 4 and 8)<= 9 A (all channels) inductive load500 mH for discrete output maximum tungsten load<25 W for discrete output maximum line resistance5 kOhm for discrete output minimum load2 mA per channel maximum leakage current1 mA, at 2 V at state 0 for discrete output communication port protocolSafe Ethernet with 2 RJ45 port(s), transmission rate: 100 Mbps, 10 Mbps, medium: dual twisted pair cable, category 5D or better exchange modeHalf duplex, full duplex, autonegotiation number of terminal blocks1 for line control outputs1 for power supply3 for discrete output4 for discrete input current consumption14 A at 24 V DC on power supply mounting support35 mm symmetrical DIN rail depth86.5 mm height109 mm width205 mm net weight1.3 kg Environment IP degree of protectionIP20 ambient air temperature for operation0…60 °C ambient air temperature for storage-40…85 °C Offer Sustainability REACh Regulation EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS Regulation WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsSize pdfSize 1.2 MBDate 7/1/07DescriptionThis manual describes the XPSMF3DIO16801 safety remote I/O. The following descriptions of the XPSMF3DIO16801 are included in this manual: - dimensions and installation - application and function - equipment description - application examplesSize pdfSize 8.2 MBDate 7/1/07DescriptionThis manual is a quick and easy start for learning XPSMFWIN. It includes anoverview of all functions and step-by-step instructions on creating a project.EU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages18
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.