Main rangeActi 9 product or component typeRemote control auxiliary device short nameRCA iC60 signal contacts composition1 OF volt-free contacts signalling circuit voltageVolt-free contact 24...230 V 0.01…1 A AC Complementary control typeRemote control impulse and maintained 230 V AC 50/60 Hz input current5 mA impulse5 mA maintained impulse duration>= 200 ms control circuit response time< 500 ms [Us] rated supply voltage230 V AC 50/60 Hz power consumption in W1 W [Ui] rated insulation voltage400 V [Uimp] rated impulse withstand voltage6 kV value of settingMode A : reclosing authorized after trippingMode B : reclosing inhibited after trippingAuto : remote control authorizedOff : remote control inhibited local signallingFlashing orange LED : not operationalFlashing green LED : ready to operate mounting modeFixed mounting supportDIN rail comb busbar and distribution block compatibilityNO 9 mm pitches7 height93 mm width63 mm depth75.5 mm product weight400 g colourWhite electrical durability10000 cycles mechanical durability10000 cycles provision for padlockingPadlockable wire stripping lengthPower supply : 10 mm (bottom)Input : 10 mm (bottom)Output : 8 mm (top) tightening torquePower supply : 1 N.mInput : 1 N.mAuxiliary output : 0.7 N.m range compatibilityActi 9: Acti 9 iC65Acti 9: Acti 9 iC60Acti 9: iMDU voltage adaptor product compatibilityIC60 2PIC60 1P + NIMDUIC60 1PIC65 1PIC65 2P Environment IP degree of protectionIP40 (in modular enclosure) conforming to IEC 60529IP20 conforming to IEC 60529 pollution degree3 conforming to IEC 60947 overvoltage categoryII tropicalisation2 relative humidity93 % at 40 °C ambient air temperature for storage-40...70 °C ambient air temperature for operation-25...60 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructions Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My Documents
No results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.