Main range of productHarmony K product or component typeCam switch body component nameK1 [Ith] conventional free air thermal current12 A sub-assembly compositionContact blocks + fixing plate cam switch functionSwitch mounting locationFront fixing modeØ 22 mm hole bezel materialPlastic Complementary [Ui] rated insulation voltage690 V (pollution degree 3) conforming to IEC 60947-1 [Ithe] conventional enclosed thermal current10 A rated operational power in W10500 W AC-21, 500 - 660 V 3 phases conforming to IEC 947-3 [Ie] rated operational current AC1 A at 500 V AC-15 conforming to IEC 947-5-1 electrical durability1000000 cycles AC-15 maximum operating rate2.5 cyc/mn AC-21 short-circuit current10000 A short-circuit protection20 A cartridge fuse, type gG [Uimp] rated impulse withstand voltage4 kV in isolating function contact operationSlow-break positive openingWith electrical connectionCaptive screw clamp terminals flexible, clamping capacity: 2 x 1.5 mm² mechanical durability1000000 cycles Environment standardsCENELEC EN 50013 product certificationsCSA 240 V 1 hp 1 phase protective treatmentTC ambient air temperature for operation-25…55 °C ambient air temperature for storage-40…70 °C shock resistance30 gn conforming to IEC 68-2-27 vibration resistance5 gn conforming to IEC 68-2-6 (f = 10…150 Hz) overvoltage categoryClass II conforming to IEC 536 IP degree of protectionIP40 conforming to IEC 529 Packing Units Package 1 Weight0.100 kg Package 1 Height0.800 dm Package 1 width0.650 dm Package 1 Length0.650 dm Offer Sustainability REACh free of SVHCYes EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS Regulation
CertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages6
Technical FAQsNo results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.