Main range of productEasyPact MVS rangeEasyPact product nameMVS40NA device short nameMVS40NA product or component typeSwitch disconnector device applicationDistribution poles description4P neutral positionLeft network typeAC suitability for isolationYes conforming to IEC 60947-2 utilisation categoryAC-23A Complementary network frequency50/60 Hz control typeElectrically operated mounting modeDrawout mounting supportBase plateRail connection positionHorizontalVertical location of connectionRear [Ie] rated operational currentAC-23A: 4000 A AC 50/60 Hz 690 V rated dutyContinuous [Ui] rated insulation voltage1000 V AC 50/60 Hz conforming to IEC 60947-3 [Uimp] rated impulse withstand voltage12 kV conforming to IEC 60947-3 [Icw] rated short-time withstand current55 kA during 1 s conforming to IEC 60947-3 at -5…70 °C30 kA during 3 s conforming to IEC 60947-3 at -5…70 °C [Icm] rated short-circuit making capacity121 kA AC at 50/60 Hz [Ue] rated operational voltage690 V AC 50/60 Hz conforming to IEC 60947-3 contact position indicatorYes mechanical durability20000 cycles with maintenance conforming to IEC 60947-310000 cycles without maintenance conforming to IEC 60947-3 electrical durabilityAC-23A: 5000000 cycles 440 V AC 50/60 Hz without maintenance conforming to IEC 60947-3AC-23A: 2500000 cycles 690 V AC 50/60 Hz without maintenance conforming to IEC 60947-3 connection pitch115 mm without spreader height439 mm width556 mm depth395 mm net weight120 kg Environment standardsIEC 60947-3 product certificationsGOSTIECCCSCCC IP degree of protectionIP40 pollution degree4 conforming to IEC 60664-1 ambient air temperature for operation-5…70 °C ambient air temperature for storage-40…85 °C without control unit Contractual warranty Warranty18 months
CatalogueFormatSizeDateAdd to My DocumentsCertificateFormatSizeDateAdd to My DocumentsDeclaration of conformityFormatSizeDateAdd to My DocumentsEnd of Life InformationFormatSizeDateAdd to My Documents
- All Languages7
Technical FAQsNo results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.