Vigi iC60 - earth leakage add-on block - 2P - 25A - 300mA - AC typeShow more characteristics >
Main rangeActi 9 product or component typeAdd-on residual current devices device short nameVigi iC60 poles description2P [In] rated current25 A earth-leakage sensitivity300 mA earth-leakage protection time delayInstantaneous Earth leakage protection typeType AC network typeAC network frequency50/60 Hz [Ue] rated operational voltage130 V AC 50/60 Hz conforming to EN 61009-1130 V AC 50/60 Hz conforming to IEC 61009-1 standardsIEC 61009-1EN 61009-1 9 mm pitches3 Complementary device location in systemOutgoer residual current tripping technologyVoltage independent [Ui] rated insulation voltage500 V AC 50/60 Hz conforming to IEC 60947-2 [Uimp] rated impulse withstand voltage6 kV conforming to IEC 60947-2 range compatibilityActi 9 iC60 product compatibilitySingle terminal local signallingTrip indicator mounting modeClip-on mounting supportDIN rail electrical connection to mcbBy screws comb busbar and distribution block compatibilityBottom : YES height91 mm depth73.5 mm product weight0.165 kg connections - terminalsTunnel type terminal downside 1 cable(s) 1...25 mm² rigid without cable endTunnel type terminal downside 1 cable(s) 1...16 mm² flexible without cable endTunnel type terminal downside 1 cable(s) 1...16 mm² flexible with cable end wire stripping length14 mm (bottom) tightening torque2 N.m (bottom) Environment IP degree of protectionIP40 modular enclosure conforming to IEC 60529IP20 conforming to IEC 60529 pollution degree3 conforming to IEC 60947-2 electromagnetic compatibility8/20 µs impulse withstand 250 A conforming to IEC 61009-1 ambient air temperature for operation-5...60 °C ambient air temperature for storage-40...85 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months 18 months
Documents and DownloadsLanguage
CADSizeAdd to My Documents
No results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.