VarSet capacitor bank Auto 350kvar xxB 400V 50HzShow more characteristics >
Main network rated voltage400 V - AC at 50 Hz415 V - AC at 50 Hz reactive power rating350 kvar operating modeAutomatic rangeVarSet device short nameVarSet automatic product or component typeCapacitor bank Complementary network pollution levelLow polluted [Gh/Sn] harmonic pollution rate15...25 % [THDU] total harmonic distorsion> 3...4 % power per step50 kvar step composition50 + 3x100 location of connectionBottom controller typeVarplus Logic VPL6 Modbus series nameVarplusCan poles description3P capacitance tolerance- 5 % to 10 % [Ui] rated insulation voltage690 V [Uimp] rated impulse withstand voltage8 kV maximum permissible voltage1.1 x Un (8 hours over 24 hours) conforming to IEC 60831 [Imp] maximum permanent currentCapacitor : 1.8 x In at 480 V conforming to IEC 60831Battery : 1.43 x In at 400 V conforming to IEC 61439-2Battery : 1.19 x In at 415 V conforming to IEC 61439-2 protection typeWithout protection [Icw] rated short-time withstand current35 kA at 1 s (Icw) step protection typeOverload: harmonic control from VarPlus LogicShort-circuit: fuse accessibility for operationFront colourRAL 7035 (grey) product weight434 kg height2200 mm width800 mm depth600 mm provided equipmentAuxiliary transformer internal voltage transformer400/230 V - 630 VA function availableGenSet shedding contactAlarm contact Environment standardsIEC 61921IEC 61439-2IEC 61439-1 product certificationsASEFACEEAC mounting locationIndoor IP degree of protectionEnvironment : IP31Safety : IPxx B IK degree of protectionIK10 relative humidity0...95 % operating altitude<= 2000 m ambient air temperature for operation-5...45 °C average ambient air temperature for operationAnnual : 35 °COver 24 hours : 45 °C Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructions
Documents and DownloadsLanguage
CatalogueSizeAdd to My Documents
No results foundUnfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.