View all Square D NEMA Relay
Control Relay with 230-250VDC Coil with 4 Overlapping ContactsShow more characteristics
8501XDO20V66Y1592 has not been replaced. Please contact your customer care center for more information.
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main Range8501X Relay TypeControl ProductRelay Complementary Coil Voltage230/250 V DC control circuit voltage limitsOperational 0.8...1.1 Uc DC rated breaking capacity6 A 120 V AC inductive control circuit UL 5083 A 240 V AC inductive control circuit UL 5081.5 A 480 V AC inductive control circuit UL 5081.2 A 600 V AC inductive control circuit UL 50810 A <= 600 V AC resistive control circuit UL 5081.1 A 125 V DC inductive control circuit UL 5084 A 125 V DC resistive control circuit UL 508 [Icm] rated short-circuit making capacity60 A 120 V AC inductive control circuit UL 50830 A 240 V AC inductive control circuit UL 50815 A 480 V AC inductive control circuit UL 50812 A 600 V AC inductive control circuit UL 50810 A <= 600 V AC resistive control circuit UL 5081.1 A 125 V DC inductive control circuit UL 5084 A 125 V DC inductive control circuit UL 508 inrush power in W18 W hold-in power consumption in W18 W operating time37 ms - pick-up21 ms - drop-out Contact Configuration2 NO + 2 NC 4 overlapping contact cartridges electrical connectionScrew clamp terminals AWG gaugeAWG 18...AWG 12 copper tightening torqueControl circuit 9.03…12.04 lbf.in (1.02…1.36 N.m) screw terminals Mounting TypePanel height90.42 mm (3.56 in) width56.64 mm (2.23 in) depth131.32 mm (5.17 in) Environment Operating Temperature-40…71 °C (-40…160 °F) CertificationsUL listed file E78403 CCN NKCRCECSA LR60905 class 3211 03 Ordering and shipping details Category21157-8501 XDO (DC) Discount ScheduleCP2 Package weight(Lbs)3.10 lb(US) (1.406 kg) ReturnabilityNo Country of originMX Contractual warranty Warranty18 months
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.