View all Square D NEMA Relay
Control Relay with 208VAC Coil with 6 NO Standard and 2 Overlapping ContactShow more characteristics
8501XO80V02Y1591 has not been replaced. Please contact your customer care center for more information.
The maximum number of products that can be compared is 4
Main Range8501X Relay TypeControl ProductRelay Complementary Coil Voltage110 V AC 50 Hz120 V AC 60 Hz control circuit voltage limitsOperational 0.85...1.1 Uc AC 50/60 Hz rated breaking capacity6 A 120 V AC inductive control circuit UL 5083 A 240 V AC inductive control circuit UL 5081.5 A 480 V AC inductive control circuit UL 5081.2 A 600 V AC inductive control circuit UL 50810 A <= 600 V AC resistive control circuit UL 5081.1 A 125 V DC inductive control circuit UL 5084 A 125 V DC resistive control circuit UL 508 [Icm] rated short-circuit making capacity60 A 120 V AC inductive control circuit UL 50830 A 240 V AC inductive control circuit UL 50815 A 480 V AC inductive control circuit UL 50812 A 600 V AC inductive control circuit UL 50810 A <= 600 V AC resistive control circuit UL 5081.1 A 125 V DC inductive control circuit UL 5084 A 125 V DC inductive control circuit UL 508 inrush power in VA148 VA 60 Hz143 VA 50 Hz hold-in power consumption in VA23 VA 60 Hz25 VA 50 Hz operating time15 ms - pick-up16 ms - drop-out Contact Configuration6 NO 6 standard contact cartridges1 NO + 1 NC 2 overlapping contact cartridges electrical connectionScrew clamp terminals AWG gaugeAWG 18...AWG 12 copper tightening torqueControl circuit 9.03…12.04 lbf.in (1.02…1.36 N.m) screw terminals Mounting TypePanel height88.90 mm (3.5 in) width56.64 mm (2.23 in) depth131.06 mm (5.16 in) Environment Operating Temperature-40…71 °C (-40…160 °F) CertificationsUL listed file E78403 CCN NKCRCECSA LR60905 class 3211 03 Ordering and shipping details Category21158-8501 XO (AC) Discount ScheduleCP2 Package weight(Lbs)2.30 lb(US) (1.043 kg) ReturnabilityNo Country of originMX Contractual warranty Warranty18 months
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.