View all I-Line Combo Panelboard
3P 200A 600V, LA FA/LA MOLDED CASE CIRCUIT BREAKERShow more characteristics
Product availabilityStock - Normally stocked in distribution facility
Main product or component typeCircuit breaker range of productI-Line Trip Unit TypeThermal-magnetic Rating CodeA Complementary Line Rated Current200 A Number of Poles3P Interrupt Rating42 kA 120 V AC42 kA 240 V AC30 kA 480Y/277 V AC [Ue] rated operational voltage600 V AC250 V DC mounting modeI-Line electrical connectionLugs loadI-Line connection line Wire GaugeAWG 1...600 kcmil aluminium/copper)1AWG 1...250 kcmil aluminium/copper)2 Terminal TypeAL400LA magnetic hold current1000 A magnetic tripping current2000 A wiring configuration3-wire height11 in (279.40 mm) width6 in (152.40 mm) depth5.84 in (148.34 mm) Environment product certificationsUL ListedCSA Ordering and shipping details Category01040 - LA/LH BRKR, SW, MAG-GARD Discount ScheduleDE2 GTIN00785901339298 ReturnabilityYes Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DIDP and DINP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Contractual warranty Warranty18 months
CatalogFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsData BulletinFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsInstruction SheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages11
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.