View all I-Line Combo Panelboard
LH MOLDED CASE CIRCUIT BREAKER, 600V, 350A, 3PShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityStock - Normally stocked in distribution facility
Main product or component typeCircuit breaker range of productI-Line Trip Unit TypeThermal-magnetic Rating CodeH Complementary Line Rated Current350 A Number of Poles3P Interrupt Rating65 kA 240 V AC35 kA 480Y/277 V AC35 kA 480 V AC25 kA 600Y/347 V AC25 kA 600 V AC50 kA 250 V DC20 kA 500 V DC 415 V AC [Ue] rated operational voltage600 V AC250 V DC500 V DC mounting modeI-Line electrical connectionLugs loadI-Line connection line Wire GaugeAWG 1...600 kcmil aluminium/copper)1AWG 1...250 kcmil aluminium/copper)2 Terminal TypeAL400LA magnetic hold current1750 A magnetic tripping current3500 A height317.50 mm (12.5 in) width152.40 mm (6 in) depth101.60 mm (4 in) Environment product certificationsCSAUL listed Ordering and shipping details Category01040 - LA/LH BRKR, SW, MAG-GARD Discount ScheduleDE2 GTIN00785901339427 Package weight(Lbs)8.29 kg (18.28 lb(US)) ReturnabilityYes Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DIDP and DINP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity ProfileNo need of specific recycling operations Contractual warranty Warranty18 months
User guideFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages4
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.