View all TeSys F Contactors
TeSys F - contactor coil - LX1FJ - 265...277 V AC 40...400 HzShow more characteristics
LX1FJ280 has not been replaced. Please contact your customer care center for more information.
Product availabilityNon-Stock - Not normally stocked in distribution facility
The maximum number of products that can be compared is 4. Remove already added products.
Main rangeTeSys product or component typeContactor coil device short nameLX1FJ range compatibilityTeSys F LC1F contactor product compatibilityLC1F400 control circuit typeAC 40...400 Hz [Uc] control circuit voltage265...277 V AC 40...400 Hz average resistance61 Ohm inrush 68 °F (20 °C)1700 Ohm holding 68 °F (20 °C) inductance of closed circuit8.1 H operating time100...170 ms opening40...75 ms closing mechanical durability10 Mcycles maximum operating rate2400 cyc/h 131 °F (55 °C) Complementary coil technologyWithout built-in suppressor module control circuit voltage limitsOperational 0.85...1.1 Uc 40...400 Hz 131 °F (55 °C))Drop-out 0.3...0.5 Uc 40...400 Hz 131 °F (55 °C)) inrush power in VA1075 VA 40...400 Hz 0.9 68 °F (20 °C)) hold-in power consumption in VA15 VA 40...400 Hz 0.3 68 °F (20 °C)) heat dissipation14 W 40...400 Hz Environment ambient air temperature for operation23…131 °F (-5…55 °C) net weight2.20 lb(US) (1 kg) Ordering and shipping details Category22341 - CONTACTOR,D,K,&F ACCESS Discount ScheduleI12 GTIN00785901082064 ReturnabilityNo Country of originCZ Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation REACh free of SVHCYes EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile Contractual warranty Warranty18 months
CatalogFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages6
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.