View all PowerPact M-Frame Molded Case Circuit Breakers
PowerPact M Molded CASE CIRCUIT BREAKER 600V 500A 3PShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Main product or component typeCircuit breaker range of productPowerPact M breaking capacity codeG trip unit technologyElectronic, basic, ET 1.0, LI accessory / separate part typeControl cable ON and OFF end Complementary current sensor rating range500 A Line Rated Current500 A [Ue] rated operational voltage600 V AC mounting modeUnit mount poles description3P breaking capacity65 kA 240 V AC35 kA 480 V AC18 kA 600 V AC continuous current rating80 % electrical connectionLugs loadLugs line AWG gaugeAWG 3/0...500 kcmil aluminium/copper)3 terminal identifierAL800M23K Environment product certificationsUL listedCSAIEC Ordering and shipping details Category01205-MG, MJ UNIT MOUNT BREAKER Discount ScheduleDE2 GTIN00785901944171 Package weight(Lbs)29.00 lb(US) (13.154 kg) ReturnabilityNo Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DIDP and DINP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins. Contractual warranty Warranty18 months
CADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages10
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.