View all PowerPact Q-Frame Molded Case Circuit Breakers
PowerPact Q - molded case circuit breaker - 2-pole - 10 kA - 240 V - 80 AShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main product or component typeCircuit breaker range of productPowerPact Q trip unit technologyThermal-magnetic Complementary Line Rated Current80 A [Ue] rated operational voltage240 V AC number of poles2 breaking capacity10 kA 240 V AC continuous current rating80 % breaking capacity codeB mounting modeI-Line electrical connectionLugs load AWG 4...300 kcmil aluminium/copperI-Line connection line BA phase connectionBA magnetic hold current1000 A magnetic tripping current1800 A height164.34 mm (6.47 in) width114.30 mm (4.5 in) depth99.82 mm (3.93 in) tightening torque247.82 lbf.in (28 N.m) 0.04…0.16 in² (25…100 mm²) AWG 4...300 kcmil) Environment product certificationsCSAUL listedIEC Ordering and shipping details Category01023 - Q2 BREAKER & SWITCH Discount ScheduleDE2 Package weight(Lbs)2.27 kg (5 lb(US)) ReturnabilityYes Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DINP and DIDP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity ProfileNo need of specific recycling operations Contractual warranty Warranty18 months
CADFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.