View all PowerPact Q-Frame Molded Case Circuit Breakers
PowerPact Q - molded case circuit breaker - 3-pole - 25 kA - 208Y/120 V - 125 AShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main product or component typeCircuit breaker range of productPowerPact Q trip unit technologyThermal-magnetic Complementary Line Rated Current125 A [Ue] rated operational voltage208Y/120 V AC number of poles3 breaking capacity25 kA 240 V AC continuous current rating80 % breaking capacity codeD mounting modeUnit mount electrical connectionLugs lineTerminal nut load AWG 4...300 kcmil aluminium/copper magnetic hold current1200 A magnetic tripping current2400 A height164.34 mm (6.47 in) width114.30 mm (4.5 in) depth99.82 mm (3.93 in) tightening torque247.82 lbf.in (28 N.m) 0.04…0.23 in² (25…150 mm²) AWG 4...300 kcmil) Environment product certificationsIECCSAUL listed Ordering and shipping details Category00187 - Q2M REPL MAIN CB Discount ScheduleDE2A GTIN00785901417217 Package weight(Lbs)2.08 kg (4.59 lb(US)) ReturnabilityNo Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DINP and DIDP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity ProfileNo need of specific recycling operations Contractual warranty Warranty18 months
CADFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.