View all PowerPact Q-Frame Molded Case Circuit Breakers
PowerPact Q - molded case circuit breaker - 3-pole - 65 kA - 240 V - 150 AShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityStock - Normally stocked in distribution facility
Main product or component typeCircuit breaker range of productPowerPact Q trip unit technologyThermal-magnetic provided equipmentPadlock handle ON and OFF end Complementary Line Rated Current150 A [Ue] rated operational voltage240 V AC number of poles3 breaking capacity65 kA 240 V AC continuous current rating80 % breaking capacity codeG mounting modeI-Line electrical connectionLugs load AWG 4...300 kcmil aluminium/copperI-Line connection line ABC phase connectionABC magnetic hold current1200 A magnetic tripping current2400 A height164.34 mm (6.47 in) width114.30 mm (4.5 in) depth99.82 mm (3.93 in) tightening torque247.82 lbf.in (28 N.m) 0.04…0.16 in² (25…100 mm²) AWG 4...300 kcmil) Environment product certificationsIECUL listedCSA Ordering and shipping details Category01023 - Q2 BREAKER & SWITCH Discount ScheduleDE2 GTIN00785901511120 Package weight(Lbs)3.05 kg (6.72 lb(US)) ReturnabilityYes Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DINP and DIDP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity ProfileNo need of specific recycling operations Contractual warranty Warranty18 months
EU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.