View all PowerPact Q-Frame Molded Case Circuit Breakers
Main product or component typeCircuit breaker range of productPowerPact Q trip unit technologyThermal-magnetic provided equipmentLug OFF endStud with nut and washer ON end Complementary Line Rated Current200 A [Ue] rated operational voltage240 V AC number of poles2 breaking capacity100 kA 240 V AC continuous current rating80 % breaking capacity codeJ mounting modeUnit mount electrical connectionLugs load AWG 4...300 kcmil aluminium/copperTerminal nut line magnetic hold current1200 A magnetic tripping current2400 A height6.47 in (164.34 mm) width4.5 in (114.30 mm) depth3.93 in (99.82 mm) tightening torque247.82 lbf.in (28 N.m) 0.04…0.23 in² (25…150 mm²) AWG 4...300 kcmil) Environment product certificationsUL ListedCSAIEC Ordering and shipping details Category00024-Q2 & QE METERING BREAKERS Discount ScheduleDE2A GTIN00785901456186 ReturnabilityYes Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DINP and DIDP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity ProfileNo need of specific recycling operations Contractual warranty Warranty18 months
CatalogFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsData BulletinFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages14
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.