View all Square D™ QO™ and QOB Miniature Circuit Breakers
Mini CB, QO, 15 A, 2P, 120/240 V, 10 kA, Plug in, CAFIShow more characteristics
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Product availabilityStock - Normally stocked in distribution facility
Main ProductArc fault detection circuit breaker RangeQO Current Rating15 A Voltage Rating120/240 V AC120 V AC Mounting TypePlug-in Number of Poles2P Circuit Breaker TypeCombination ARC-fault RatingsNot rated Electrical ConnectionPressure plate type of packingClam packaging Complementary Inturrupt Rating10 kA 120/240 V AC 50/60 Hz 10 kA 120 V AC 50/60 Hz Number of Panel Spaces2 Wire SizeAWG 14...AWG 8 copperAWG 12...AWG 8 aluminium height120.65 mm (4.75 in) depth73.91 mm (2.91 in) width38.10 mm (1.5 in) Environment CertificationsUL listedCSA Ambient Rating104 °F (40 °C) Ordering and shipping details Category06303 - QO SINGLE POLE ARC FAULT CIRCUIT BREAKER Discount ScheduleDE2A GTIN00785901389477 Package weight(Lbs)0.45 kg (1 lb(US)) ReturnabilityYes Country of originMX Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals which are known to the State of California to cause Carcinogen & Reproductive harm. For more information go to www.p65warnings.ca.gov EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity Profile
CatalogFormatSizeAdd to My DocumentsInstruction SheetFormatSizeAdd to My DocumentsSize pdfSize 613.1 KBDate 6/18/19DescriptionThis bulletin is an instruction sheet for the installation and removal of the Square D™ QO™ and QOB Combination Arc Fault Circuit Interrupter (CAFI).China RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages8
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.