View all Modicon Premium PAC
Main range of productModicon Premium Automation platform product or component typeDiscrete input module discrete input number16 capacitive isolated EN/IEC 61131-2 type 2 discrete input voltage220 V AC network frequency50/60 Hz 47…63 Hz AC sensor power supply170…264 V input compatibilityWith 2-wire/3-wire proximity sensors EN/IEC 60947-5-2 discrete input current15 mA Complementary voltage state 1 guaranteed159 V current state 1 guaranteed6 mA voltage state 0 guaranteed40 V current state 0 guaranteed4 mA input impedance20000 Ohm at state 1 response time<= 20 ms10 ms isalotion resistance< 10 MOhm 500 V DC power dissipation0.97 W electrical connectionScrew terminal markingCE current consumption80 mA 5 V DC module formatStandard net weight0.79 lb(US) (0.36 kg) Environment dielectric strength1500 V AC 50/60 Hz standards92/31/EEC73/23/EECCSA C22.2 No 213 Class I Division 2 Group A93/68/EECEN/IEC 61131-289/336/EECCSA C22.2 No 213 Class I Division 2 Group BCSA C22.2 No 213 Class I Division 2 Group DIEC 60664UL 508CSA C22.2 No 213 Class I Division 2 Group CCSA C22.2 No 142 product certificationsGLRINARMRSABSBVDNVLR ambient air temperature for operation32…140 °F (0…60 °C) ambient air temperature for storage-13…158 °F (-25…70 °C) relative humidity10…95 % without condensation for operation5…95 % without condensation for storage operating altitude0...6561.68 ft (0...2000 m) protective treatmentTC IP degree of protectionIP20 pollution degree2 Ordering and shipping details Category22558 - TSX PREMIUM, ATRIUM & PL7 PRO Discount SchedulePC22 GTIN00785901725497 Package weight(Lbs)3.00 kg (6.61 lb(US)) ReturnabilityNo Country of originFR Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: Lead and lead compounds which is known to the State of California to cause cancer and birth defects or other reproductive harm.For more information go to www.p65warnings.ca.gov Contractual warranty Warranty18 months
- All Languages1
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.