View all Modicon Premium PAC
Main range of productModicon Premium Automation platform product or component typeDiscrete input module discrete input number32 current sink isolated EN/IEC 61131-2 type 1 discrete input voltage24 V DC positive sensor power supply19…30 V discrete input current3.5 mA Complementary voltage state 1 guaranteed>= 11 V current state 1 guaranteed>= 3 mA voltage state 0 guaranteed<= 5 V current state 0 guaranteed<= 1.5 mA input impedance6300 Ohm at state 1 response time<= 7 ms4 ms isalotion resistance< 10 MOhm 500 V DC power dissipation(1 W + 0.1 W x No of channels used) electrical connectionHE-10 connector markingCE current consumption135 mA 5 V DC160 mA 24 V DC module formatStandard net weight0.66 lb(US) (0.3 kg) Environment dielectric strength1500 V AC 50/60 Hz standardsCSA C22.2 No 213 Class I Division 2 Group BIEC 60664CSA C22.2 No 142CSA C22.2 No 213 Class I Division 2 Group A92/31/EECEN/IEC 61131-2UL 508CSA C22.2 No 213 Class I Division 2 Group D93/68/EECCSA C22.2 No 213 Class I Division 2 Group C73/23/EEC89/336/EEC product certificationsLRGLBVRMRSRINAABSDNV ambient air temperature for operation32…140 °F (0…60 °C) ambient air temperature for storage-13…158 °F (-25…70 °C) relative humidity10…95 % without condensation for operation5…95 % without condensation for storage operating altitude0...6561.68 ft (0...2000 m) protective treatmentTC IP degree of protectionIP20 pollution degree2 Ordering and shipping details Category22558 - TSX PREMIUM, ATRIUM & PL7 PRO Discount SchedulePC22 GTIN00785901871040 Package weight(Lbs)0.41 kg (0.9 lb(US)) ReturnabilityNo Country of originFR Offer Sustainability California proposition 65WARNING: This product can expose you to chemicals including: Lead and lead compounds which is known to the State of California to cause cancer and birth defects or other reproductive harm.For more information go to www.p65warnings.ca.gov Contractual warranty Warranty18 months
CADFormatSizeAdd to My Documents
- All Languages1
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.