View all PowerPact P-Frame Molded Case Circuit Breakers
circuit breaker Compact NS1000H - Micrologic 2.0 A - 1000 A - 3 poles 3tShow more characteristics
33248 has not been replaced. Please contact your customer care center for more information.
* Price is “List Price” and may be subject to a trade discount – check with your local distributor or retailer for actual price.
Add to My Products Remove from My Products
The maximum number of products that can be compared is 4
Main rangeCompact range of productNS630b...1600 product or component typeCircuit breaker device short nameCompact NS1000H device applicationDistribution poles description3P protected poles description3t network typeAC breaking capacity codeH suitability for isolationYes IEC 60947-2 utilisation categoryCategory B trip unit nameMicrologic 2.0 A trip unit technologyElectronic trip unit rating1000 A 122 °F (50 °C) Complementary network frequency50/60 Hz control typeRotary handleToggle mounting modeFixed mounting supportBackplate upside connectionFront downside connectionFront (In) rated current up to 65 °C1000 A 122 °F (50 °C) [Ui] rated insulation voltage800 V AC 50/60 Hz IEC 60947-2 [Uimp] rated impulse withstand voltage8 kVIEC 60947-2 [Ue] rated operational voltage690 V AC 50/60 Hz IEC 60947-2 circuit breaker CT rating1000 A breaking capacity42 kA Icu 660/690 V AC 50/60 Hz IEC 60947-265 kA Icu 440 V AC 50/60 Hz IEC 60947-270 kA Icu 380/415 V AC 50/60 Hz IEC 60947-285 kA Icu 220/240 V AC 50/60 Hz IEC 60947-250 kA Icu 500/525 V AC 50/60 Hz IEC 60947-2 [Ics] rated service breaking capacity52 kA 380/415 V AC 50/60 Hz IEC 60947-231 kA 660/690 V AC 50/60 Hz IEC 60947-237 kA 500/525 V AC 50/60 Hz IEC 60947-248 kA 440 V AC 50/60 Hz IEC 60947-252 kA 220/240 V AC 50/60 Hz IEC 60947-2 auxiliary contact composition1 NO/NC mechanical durability10000 cycles electrical durability2000 cycles 690 V AC 50/60 Hz In IEC 60947-2 4000 cycles 690 V AC 50/60 Hz In/2 IEC 60947-2 5000 cycles 440 V AC 50/60 Hz In IEC 60947-2 6000 cycles 440 V AC 50/60 Hz In/2 IEC 60947-2 local signallingPositive contact indication [Icw] rated short-time withstand current19.2 kA trip unit protection functionsLI protection typeOverload protection (long time)Instantaneous short-circuit protection long time pick-up adjustment type IrAdjustable long time pick-up adjustment range0.4...1 x In long time delay adjustment typeAdjustable 9 settings [tr] long-time delay adjustment range0.7…16.6 s 7.2 x Ir12.5…600 s 1.5 x Ir0.5…24 s 6 x Ir thermal memory20 mn instantaneous pick-up adjustment type IiAdjustable instantaneous pick-up adjustment range1.5...10 x Ir integrated instantaneous protection40 kA zone selective interlocking ZSIWith display typeLCD display type of measurementAmmeter height12.87 in (327 mm) width8.27 in (210 mm) depth5.79 in (147 mm) Environment standardsIEC 60947-2 product certificationsASTAASEFA power losses22 W IP degree of protectionIP40 IEC 60529 IK degree of protectionIK07 EN 50102 pollution degree3 IEC 60947 ambient air temperature for operation-13…158 °F (-25…70 °C) ambient air temperature for storage-58…185 °F (-50…85 °C) Ordering and shipping details Category01215-PG,H,J,K,L,N UNIT MT BREAKERS Discount ScheduleDE2 GTIN03303430332480 Package weight(Lbs)26.21 lb(US) (11.890 kg) ReturnabilityNo Country of originIT Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity ProfileNo need of specific recycling operations WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins. Contractual warranty Warranty18 months
China RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.