View all PowerPact P-frame Molded Case Circuit Breakers
MOLDED CASE CIRCUIT BREAKER 600V 1200AShow more characteristics
Product availabilityNon-Stock - Not normally stocked in distribution facility
Main product or component typeCircuit breaker range of productPowerPact P current sensor rating range1200 A Line Rated Current1200 A breaking capacity65 kA 240 V AC35 kA 480 V AC18 kA 600 V AC trip unit technologyElectronic, power, Micrologic 5.0 P, LSI Complementary product certificationsUL ListedCSAIEC [Ue] rated operational voltage600 V AC module typeP-Frame mounting locationBusbar mounting modeUnit mount poles description3P breaking capacity codeG electrical connectionBusbar connection lineBusbar connection load continuous current rating100 % device short nameA communication interfaceModbus height16.16 in (410.46 mm) depth8.05 in (204.47 mm) width8.27 in (210.06 mm) tightening torque442.54 lbf.in (50 N.m) 0.15…0.37 in² (95…240 mm²) AWG 3/0...500 kcmil)8.85…11.51 lbf.in (1.0…1.3 N.m) Ordering and shipping details Category01215 - PG,H,J,K,L,N UNIT MT BREAKERS Discount ScheduleDE2 GTIN00785901618539 ReturnabilityYes Country of originUS Offer Sustainability Sustainable offer statusGreen Premium product California proposition 65WARNING: This product can expose you to chemicals including: DINP and DIDP which is known to the State of California to cause Carcinogen and Reproductive harm. For more information go to www.p65warnings.ca.gov REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information.
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins. Contractual warranty Warranty18 months
China RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.