Main rangePrisma product namePrisma G IP degree of protectionIP55 with door product or component typeEnclosure enclosure typeFunctional enclosure delivered in kit form device applicationLow voltage electrical distribution enclosure mountingSurface type of front plateWithout to be ordered separately number of vertical modules [50 mm]33 number of 18 mm modules per row36 Complementary installation descriptionFloor-standing enclosure - width 850 mm [Ui] rated insulation voltage1000 V on main rear busbars conforming to IEC 61439-2 [In] rated current630 A at 40 °C conforming to IEC 61439-2 [Icw] rated short-time withstand current25 kA 1 s conforming to IEC 61439-2 [Ipk] rated peak withstand current53 kA conforming to IEC 61439-2 network frequency50/60 Hz enclosure materialRear panel: treated sheet steel additional informationCan be combined side by side quantity per setSet of 1 height1750 mm width745 mm depth260 mm net weight40 kg surface finishMattSmooth colourWhite (RAL 9001) Environment IK degree of protectionIK10 with door conforming to EN/IEC 62262 protective treatmentElectrophoresis treatment and hot-polymerised polyester epoxy powder standardsIEC 61439-1IEC 61439-2IEC 62208 mechanical robustnessSeismic tests - 2.5G conforming to IEC 60068-2-57 Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Pro-active China RoHS declaration (out of China RoHS legal scope)
Environmental Disclosure Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
- All Languages9
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.