View all Acti 9 iME
Main rangeActi 9 range of productIME1 device short nameIME1zr product or component typeActive energy hour meter Complementary poles description1P + N type of measurementActive power device applicationPartial meterSub billing accuracy classClass 1 active energy conforming to IEC 62053-21 input typeDirect input [In] rated current63 A rated voltage230 V +/- 20 % network frequency50 Hz60 Hz technology typeElectronic display typeLCD display sampling rate32 samples/cycle display digits5 maximum value measured999.99 MWh communication port support- local signallingYellow indicator light: metering and activity number of outputs1 pulse output voltage24 V DC@18 mA230 V AC@100 mA impulse duration200 ms power consumption in VA2.5 VA mounting modeClip-on mounting supportDIN rail connections - terminalsTunnel type terminals 1 cable(s) 16 mm² bottom for power circuitTunnel type terminals 1 cable(s) 6 mm² top for remote transfer tightening torquePower circuit: 1.5 N.mRemote transfer: 0.9 N.m standardsIEC 61557-12IEC 62053-21 Environment IP degree of protectionIP50 conforming to IEC 60529 IK degree of protectionIK05 colourWhite 9 mm pitches4 width36 mm height81 mm depth65 mm net weight0.135 kg Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectiveCompliant
EU RoHS Declaration
Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsSize pdfSize 12.3 MBDate 1/25/20DescriptionNote that no printed catalogs are available but all necessary source files, in 13 sections, are available for download from the Shopping Kiosk.CADFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
- All Languages9
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.