Main rangeActi 9 product nameActi 9 iID product or component typeResidual current circuit breaker (RCCB) device short nameIID poles description2P neutral positionLeft [In] rated current80 A network typeAC earth-leakage sensitivity300 mA earth-leakage protection time delayInstantaneous earth-leakage protection classType AC Complementary device location in systemOutgoer network frequency50 Hz [Ue] rated operational voltage230...240 V AC 50/60 Hz residual current tripping technologyVoltage independent rated breaking and making capacityIdm 1500 AIm 1500 A rated conditional short-circuit current10 kA [Ui] rated insulation voltage500 V AC 50/60 Hz [Uimp] rated impulse withstand voltage6 kV contact position indicatorYes control typeToggle mounting modeClip-on mounting supportDIN rail 9 mm pitches4 height96 mm width36 mm depth74.5 mm net weight0.21 kg colourWhite mechanical durability20000 cycles electrical durabilityAC-1: 10000 cycles locking options descriptionPadlocking device connections - terminalsSingle terminal top or bottom1…35 mm² rigidSingle terminal top or bottom1…25 mm² flexibleSingle terminal top or bottom1…25 mm² flexible with ferrule wire stripping length14 mm for top or bottom connection tightening torque3.5 N.m top or bottom Environment standardsGB 16916.21EN/IEC 61008-1 IP degree of protectionIP20 conforming to IEC 60529IP40 (modular enclosure) conforming to IEC 60529 pollution degree3 electromagnetic compatibility8/20 µs impulse withstand, 250 A conforming to EN/IEC 61008-1 ambient air temperature for operation-25…60 °C ambient air temperature for storage-40…85 °C Offer Sustainability REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Contractual warranty Warranty18 months
EU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My DocumentsREACh DeclarationFormatSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.