Main rangePowerLogic product namePowerLogic BCPMSC product or component typeMulti-circuit energy meter device short nameBCPMSCA Model typeAdvanced power monitoringBasic instrumentation energy managementSub billing and cost allocation device applicationSub billing power quality analysisvoltage sag and swell detection type of measurementVoltageCurrentFrequencyActive powerPower factorActive energy [Us] rated supply voltage90...277 V AC 50/60 Hz +/- 1 % network frequency60 Hz50 Hz Complementary current transformer inputSplit core CT 0.333 V42 x update time1.8 s measurement voltage90…277 V phase to neutral150…480 V phase to phase measurement accuracyBranch current 2 % 0.25…2 ABranch current 1 % 2…100 AMains current 3 % 1…100 %Mains current 3 % 2…100 %Voltage 1 % 90…277 V sampling rate256 samples/cycle provided equipment42 x current transformer2 x cables2 x adapter board communication port protocolModbus RTU communication port supportRS485 communication of dataHigh current alarmLow current alarmUnder voltage alarmHigh-high current alarmLow-low current alarmOver voltage alarm Environment mounting modeClip-on mounting supportBoard relative humidity95 % at 0…60 °C ambient air temperature for storage-40…70 °C operating altitude3000 m standardsIEC 61036EN 61010ANSI C12.1UL 508 product certificationsUL width288 mm height146 mm net weight1.5 kg Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
China RoHS Regulation WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsSize pdfSize 12.9 MBDate 9/17/19DescriptionNote that no printed catalogs are available but all necessary source files, in 14 sections, are available for download from the Shopping Kiosk.Catalogue pageFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages7
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.