Main range of productActi 9 product nameActi 9 STD product or component typeRemote control dimmer device short nameSTD product compatibilityPower regulators designed function availableAutomatic load type detection Complementary device applicationBuilding load type230 V AC halogen lamp: 40...400 W230 V AC incandescent lamp: 40...400 W low voltage halogen lamp with electronic transformer: 40...400 W motor: 40...200 W low voltage halogen lamp with conventional transformer: 40...400 W low voltage halogen lamp with toroidal transformer: 40...300 W control typeLocal control: push-buttonRemote control: push-button power consumption in VA0.8 VA thermal losses3 W [Ue] rated operational voltage230 V AC +/- 10 % at 50 Hz protection typeElectronic overload protectionElectronic over temperature protectionElectronic overvoltage protectionSingle shot thermal fuse mounting supportDIN rail 9 mm pitches4 connected auxiliariesMaximum 25 auxiliary push-buttons without light indication, distance : < 50 mMaximum 5 auxiliary push-buttons with light indication, distance : < 50 m connections - terminalsScrew terminals, 2 cable(s) 4 mm² top height85 mm width36 mm depth62 mm net weight80 g Environment IP degree of protectionIP20 standardsEN 60669-2-1 directives73/23/EEC - low voltage directive89/336/EEC - electromagnetic compatibility ambient air temperature for operation0…70 °C ambient air temperature for storage0…60 °C Offer Sustainability REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure Contractual warranty Warranty18 months
User guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsBrochureFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsCatalogue pageFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages13
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.