Main range of productCanalis range compatibilityKS busbar trunking product or component typeTap-off unit busbar trunking compatibilityCanalis KS busbar trunkingplug-in [Ie] rated operational current630 A at 35 °C protection typefuse isolator: blade type fuse, size 3 conforming to NF or DIN provided equipmentfuse to be ordered separately mounting modePlug-in with fixed polarity tap-off unit polarity3L+PEN colourWhite (RAL 9001) Complementary device applicationMedium power distribution [Uimp] rated impulse withstand voltage6.8 kV [Ui] rated insulation voltage500 V depending on protective device network frequency50/60 Hz electrical connectionCopper cable lug - ISO40 480 mm² flexibleCopper cable lug - ISO40 480 mm² rigid door/cover opening sideRight tap-off unit disconnection modeBy opening the door standardsIEC 61439-1IEC 61439-6 body materialMetal width1144.5 mm depth300 mm depth (door open)1106.5 mm height611 mm net weight59 kg Environment earthing systemTN-C IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 Packing Units Package 1 Weight57.000 kg Package 1 Height3.710 dm Package 1 width6.300 dm Package 1 Length11.050 dm Offer Sustainability Sustainable offer statusGreen Premium product EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Environmental Disclosure WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My DocumentsCADFormatSizeAdd to My DocumentsCertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsDeclaration of conformityFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My DocumentsProduct Environmental ProfileFormatSizeAdd to My Documents
- All Languages11
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.