Main rangeCanalis product nameKT product or component typeBusbar trunking busbar descriptionDistribution length device short nameKTA tap-off unit compatibilityPlug-in tap-off unit from Canalis KSPlug-in tap-off unit from Canalis KT device applicationHigh power distribution materialAluminium [Ie] rated operational current2500 A at 35 °C polarity3L + N + PER number of tap-off outlets1 nominal output current25…630 A earth conductorReinforced short-circuit levelReinforced version length2500…3000 mm provided equipmentJointing unitTrunking unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current113 kA [Ipk] rated peak withstand current248 kA electrical connectionSliding contact radiated magnetic field1.6 µT thermal stress limit12769 A².s THDI0…15 % 2500 A15…33 % 3200 A33…100 % 4000 A maximum voltage drop<0.0024 V with power factor = 1 at 50 Hz with 1A for 100 m long <0.0025 V with power factor = 0.9 at 50 Hz with 1A for 100 m long <0.0024 V with power factor = 0.8 at 50 Hz with 1A for 100 m long <0.0022 V with power factor = 0.7 at 50 Hz with 1A for 100 m long mounting modeBy hook mounting supportPendantCantilever arm installation directionHorizontalVertical neutral positionRight standardsIEC 61439-1IEC 61439-6 dimension typeMade to measure width140 mm height244 mm colourGrey (RAL 7035) linear load36 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor0…35 °C (100 % of In)35…40 °C (97 % of In)40…45 °C (93 % of In)45…50 °C (90 % of In)50…55 °C (86 % of In)
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My Documentsprp.document.label.format zipSize 2.3 MBDate 8/1/17Instruction sheetFormatSizeAdd to My Documents
- All Languages8
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.