Main rangeCanalis product nameKT product or component typeCenter feeder trunking device short nameKTA device applicationFeeder length supplyDry-type transformer materialAluminium [Ie] rated operational current3200 A at 35 °C neutral positionRight earth conductorReinforced short-circuit levelStandard version provided equipmentTrunking unit Complementary housing materialPolyester film contacts materialCopper [Ue] rated operational voltage1000 V network frequency50/60 Hz [Ui] rated insulation voltage1000 V [Icw] rated short-time withstand current86 kA [Ipk] rated peak withstand current189 kA radiated magnetic field2.1 µT thermal stress limit7396 A².s THDI0…15 % 3200 A15…33 % 4000 A maximum voltage drop<0.0018 V with power factor = 1 at 50 Hz with 1A for 100 m long <0.0019 V with power factor = 0.9 at 50 Hz with 1A for 100 m long <0.0018 V with power factor = 0.8 at 50 Hz with 1A for 100 m long <0.0017 V with power factor = 0.7 at 50 Hz with 1A for 100 m long mounting modeBy screws mounting supportPlate polarity3L + N + PER number of tap-off outlets0 standardsIEC 61439-1IEC 61439-6 dimension typeMade to measure connection pitch470…700 mm bar width200 mm depth140 mm height584 mm lengthdirection 1: 260 mm1680 mm colourWhite (RAL 9001) linear load37 kg/m Environment IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 derating factor0…35 °C (100 % of In)35…40 °C (97 % of In)40…45 °C (93 % of In)45…50 °C (90 % of In)50…55 °C (86 % of In) Packing Units Unit Type of Package 1PCE Number of Units in Package 11 Package 1 Weight57.05 kg Package 1 Height50 cm Package 1 width13.8 cm Package 1 Length190 cm
CatalogueFormatSizeAdd to My DocumentsUser guideFormatSizeAdd to My DocumentsCADFormatSizeAdd to My Documentsprp.document.label.format zipSize 588.1 KBDate 1/7/14CertificateFormatSizeAdd to My DocumentsInstruction sheetFormatSizeAdd to My Documents
- All Languages12
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.