Main rangeTeSys product nameTeSys F product or component typeStar delta starter device short nameLC3F contactor applicationMotor control utilisation categoryAC-3 device presentationPre-wired poles description3 x 3P power pole contact composition3 x 3 NO [Ue] rated operational voltagePower circuit: <= 1000 V AC 16 Hz 2/3...200 Hz [Ie] rated operational current400 A (at <55 °C) at <= 440 V AC AC-3 for power circuit motor power kW185 kW at 220/230 V AC 50/60 Hz315 kW at 380/400 V AC 50/60 Hz355 kW at 415 V AC 50/60 Hz375 kW at 440 V AC 50/60 Hz control circuit typeAC at 50/60 Hz [Uc] control circuit voltage415 V AC 50/60 Hz auxiliary contact composition1 NC for KM1 star contactor1 NO for KM1 star contactor2 NC for KM2 line contactor1 NO for KM2 line contactor1 NC for KM3 delta contactor2 NO for KM3 delta contactor [Uimp] rated impulse withstand voltage8 kV [Ui] rated insulation voltage1000 V conforming to IEC 60947-4-11500 V conforming to VDE 0110 group C interlocking typeMechanical mounting supportPlate standardsIEC 60947-4-1JIS C8201-4-1IEC 60947-1EN 60947-1EN 60947-4-1 product certificationsABSCSALROS (Lloyds register of shipping)ULRINACCCCBRMRoSDNV Complementary [Ith] conventional free air thermal current500 A 40 °C Irms rated making capacity4000 A conforming to IEC 60947-4-1 rated breaking capacity3200 A conforming to IEC 60947-4-1 [Icw] rated short-time withstand current3600 A 40 °C - 10 s2400 A 40 °C - 30 s1700 A 40 °C - 1 min1200 A 40 °C - 3 min1000 A 40 °C - 10 min associated fuse rating500 A gG at <= 440 V400 A aM at <= 440 V connections - terminalsControl circuit: screw clamp terminals 1 1…4 mm² - cable stiffness: flexible with cable endControl circuit: screw clamp terminals 2 1…2.5 mm² - cable stiffness: flexible with cable endControl circuit: screw clamp terminals 1 1…4 mm² - cable stiffness: flexible without cable endControl circuit: screw clamp terminals 2 1…4 mm² - cable stiffness: flexible without cable endControl circuit: screw clamp terminals 1 1…4 mm² - cable stiffness: solid without cable endControl circuit: screw clamp terminals 2 1…4 mm² - cable stiffness: solid without cable endPower circuit: bar 2 - busbar cross section: 30 x 5 mmPower circuit: bolted connectionPower circuit: lugs-ring terminals 2 150 mm² connections bolt diameterM10 tightening torqueControl circuit: 1.2 N.mPower circuit: 35 N.m operating time40...65 ms closing100...170 ms opening mechanical durability10 Mcycles maximum operating rate2400 cyc/h 55 °C starting time30 s control circuit voltage limitsOperational: 0.85...1.1 Uc at 40...400 Hz (at <55 °C)Drop-out: 0.35...0.55 Uc at 40...400 Hz (at <55 °C) inrush power in VA1075 VA 40...400 Hz cos phi 0.9 (at 20 °C) hold-in power consumption in VA15 VA 40...400 Hz cos phi 0.9 (at 20 °C) heat dissipation14 W width725 mm height180 mm depth276 mm net weight37.125 kg Environment IP degree of protectionIP20 front face with shrouds conforming to IEC 60529IP20 front face with shrouds conforming to VDE 0106 protective treatmentTH ambient air temperature for storage-60…80 °C ambient air temperature for operation-5…55 °C-40…70 °C at Uc operating altitude3000 m with derating factor mechanical robustnessShocks contactor closed: 15 Gn for 11 msVibrations contactor closed: 5 Gn, 5...300 HzShocks contactor open: 6 Gn for 11 msVibrations contactor open: 1.5 Gn, 5...300 Hz Offer Sustainability EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
PVC freeYes Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My Documentsprp.document.label.format pdfSize 111.5 MBDate 7/12/19DescriptionReady-to-use motor starters and all components for building specific motor starters ( circuit breakers, contactors, overload relays , accessories ...).The catalogue can also be downloaded chapter per chapter.China RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages5
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.