View all TeSys LG, LJ Enclosed Safety Starters
TeSys LG - enclosed DOL starter - 9...14 A - 400 V AC coilShow more characteristics
LG1D122V716 has not been replaced. Please contact your customer care center for more information.
The maximum number of products that can be compared is 4. Remove already added products.
Main rangeTeSys product nameTeSys LG device short nameLG1D product or component typeEnclosed DOL starter device applicationSafety utilisation categoryAC-3 device compositionContactorSwitch disconnectorCircuit-breaker motor power kW3 kW at 220/230 V AC 50/60 Hz5.5 kW at 400/415 V AC 50/60 Hz5.5 kW at 440 V AC 50/60 Hz thermal protection adjustment range9…14 A [Uc] control circuit voltage400 V AC 50/60 Hz control typePush-button start white IPush-button stop black ORotary handle emergency stop red Complementary cable entry number4 2 Pg 13 + 2 Pg 16 top4 2 Pg 13 + 2 Pg 16 bottom width175 mm height165 mm depth165 mm net weight1.27 kg Environment standardsIEC 60204-1IEC 60947-4-1 materialPolycarbonate IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK07 conforming to IEC 60529 environmental characteristicStandard environment Offer Sustainability REACh Regulation REACh free of SVHCYes EU RoHS DirectiveCompliant
EU RoHS Declaration
Toxic heavy metal freeYes Mercury freeYes RoHS exemption information China RoHS Regulation WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
CatalogueFormatSizeAdd to My Documentsprp.document.label.format pdfSize 111.5 MBDate 7/12/19DescriptionReady-to-use motor starters and all components for building specific motor starters ( circuit breakers, contactors, overload relays , accessories ...).The catalogue can also be downloaded chapter per chapter.CADFormatSizeAdd to My DocumentsChina RoHS declarationFormatSizeAdd to My DocumentsEU RoHS DeclarationFormatSizeAdd to My Documents
- All Languages6
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.