XULM06031H7 is replaced by the following group of products:
- Reason for Substitution: End of life
- Substitution date: 01 January 2016
Main range of productOsiSense XU series nameGeneral purpose single mode electronic sensor typePhoto-electric sensor sensor nameXUL sensor designCompact detection systemReflex materialPlastic type of output signalDiscrete supply circuit typeAC/DC wiring technique5-wire discrete output function1 NC electrical connectionCable cable length2 m product specific application- emissionInfrared reflex [Sn] nominal sensing distance6 m reflex need reflector XUZC80 Complementary enclosure materialABS lens materialPMMA maximum sensing distance9 m with reflector Ø 80 mm output typeRelay add on outputWithout cable composition5 x 0.34 mm² wire insulation materialPVC cable outer diameter6 mm status LED1 LED for output state [Us] rated supply voltage24...240 V AC/DC supply voltage limits20…264 V AC/DC output voltage<= 250 V switching capacity in mA<= 100 mA (overload and short-circuit protection) switching frequency<= 20 Hz current consumption<= 40 mA no-load maximum delay first up60 ms maximum delay response25 ms maximum delay recovery25 ms setting-upWithout sensitivity adjustment electrical durability500000 cycles, cos f = 1, operating rate <60 cyc/mn at 250 V500000 cycles, cos f = 0.4, operating rate <60 cyc/mn at 250 V depth45 mm height70 mm width18 mm kit compositionBracket XULZ41Sensor Environment product certificationsURCSA ambient air temperature for operation-25…55 °C ambient air temperature for storage-40…70 °C vibration resistance7 gn, amplitude = +/- 2 mm (f = 10…55 Hz) conforming to IEC 60068-2-6 shock resistance20 gn (duration = 11 ms) conforming to IEC 60068-2-27 IP degree of protectionIP67 conforming to IEC 60529IP671 conforming to NF C 20-010 Contractual warranty Warranty18 months
Instruction sheetFormatSizeAdd to My DocumentsEnd of Life InformationFormatSizeAdd to My Documents
- All Languages3
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.